|當前位置 -> 熱風爐首頁－ 熱風爐知識－ 全面論述生物質熱風爐啟動注意事項 發布時間︰(2018/12/9)關鍵詞︰熱風爐|
啟動注意事項有以下三大點︰一 在上水過程中應檢查鍋筒、集箱的孔門及各部的閥門、法蘭、堵頭等是否有漏水現象。當發現漏水時應停止上水並進行處理。當水位升至鍋筒水位計的負100毫米處，停止上水。以後水位應不變，若水位有明顯變化，應查明原因予以消除。二 要求整個升溫升壓過程力求平緩、均勻，並在以下各個階段檢查記錄膨脹指示值。
There are three points for attention in the start-up of biomass hot blast stove: First, in the process of water supply, it is necessary to check whether there are leakage phenomena in the pot drum, header orifices, valves, flanges, plugs, etc. When leakage is found, the water should be stopped and treated. When the water level of the hot blast stove rises to the negative 100mm of the drum water level gauge, the water supply is stopped. After that, the water level should remain unchanged. If the water level changes obviously, the reasons should be found out and eliminated.
Secondly, the whole process of temperature and pressure rise should be smooth and uniform, and the expansion indicators should be checked and recorded in the following stages.
Before and after Sheung Shui. When the drum pressure reaches 0.3-0.4, 10. -1.5, 2.0 and 3.9 MPA respectively, check the expansion. If abnormal expansion is found, the cause must be found out and the abnormal situation must be eliminated before the pressure can continue to rise.
Attention should be paid to the merging of three hot stoves
1. Keep the main steam pressure lower than the steam main pipe pressure 0.05-0.1 MPA in parallel furnace. If the steam pressure of hot blast furnace is higher than the main pipe pressure, it is forbidden to combine furnace.
When parallel, the steam temperature should be lower than the rated value of 30.C, maintain a lower water level, stable combustion, and pay attention to keeping the parameters of steam pressure and temperature, and slowly increase the evaporation.
3 在並列過程 中，如引起汽機的汽溫急劇下降時或發生蒸汽管道水沖擊時，應立即停止並爐，減弱燃燒，加強 水，待恢復正 ︰籩匭虜 。
3 In the process of parallel operation, if the steam temperature of the turbine drops sharply or the water shock of the steam pipeline occurs, the furnace should be stopped immediately, the combustion should be weakened, the water should be strengthened, and the parallel operation should be restored to normal.
After parallel arrangement, the hot blast stove units shall be thoroughly inspected, and the main operation and newly discovered problems during ignition to parallel arrangement shall be recorded in the relevant record book.
5. Close the recirculation valve when the feed pump starts to supply water.
|相關閱讀︰环亚APP下载熱風爐煤質究竟該怎樣掌控 | 熱水熱風爐線磨損量以及水溫控制 | 燃氣熱風爐種類特點以及工作原理|
版權所有︰無錫市ag环亚娱乐平台干燥設備有限公司主營︰熱風爐 電話︰0510-83955910 傳真︰0510-83051522 技術支持︰易商科技